The VMS range offers a versatile solution with a superb Icw rating. As a single phase support, they can be installed to suit your application. Whether AC or DC.
The VMS range of supports achieve fault ratings of up to Icw rating of 100 kA/1 s.
Each support can hold one, two or three conductors, and can be used without spacers to give any desired conductor centres or with spacers to create 110 mm, 122.5 mm and 130 mm conductor centres.
- Up to 100 kA/1 s fault rating
- Single phase units to give a wide scope for design and application
- UL Recognised Component; File Number: E505645
VMS Busbar Supports & Spacers
VMS3-10, VMS-S110, VMS-S122.5 & VMS-S130
† In line with the limits set out in IEC 61439, insulating components in contact with conductors may be required to continuously operate at an average of 140 °C (max. 145 °C).
This range of products meets the requirement, the material for them being assigned thermal class F established using methods similar to IEC 60085.
|Part Number||3D Model||Conductors||Support|
|VMS3-10||VMS3-10 STEP file||2 × 100×10||110||65 kA||3 s||VMS-S110||VMS-S110 STEP file||Optional|
|VMS3-10||VMS3-10 STEP file||2 × 100×10||110||80 kA||1 s||VMS-S110||VMS-S110 STEP file||Optional|
|VMS3-10||VMS3-10 STEP file||2 × 100×10||122.5||80 kA*#||1 s||VMS-S122.5||VMS-S122.5 STEP file||Optional|
|VMS3-10||VMS3-10 STEP file||2 × 100×10||130||65 kA||3 s||VMS-S130||VMS-S130 STEP file||Optional|
|VMS3-10||VMS3-10 STEP file||2 × 100×10||130||80 kA||1 s||VMS-S130||VMS-S130 STEP file||Optional|
|VMS3-10||VMS3-10 STEP file||2 × 100×10||130||100 kA||1 s||VMS-S130||VMS-S130 STEP file||Required|
* Fault level extrapolated from data achieved for the VMS-S110
# Part not included in UL Recognised Component File
Termate is committed to the highest standard of Customer Focus and we have made every effort to maintain the accuracy and completeness of the information provided in this catalogue. Where improvements to our products affect their installation and usage we endeavour to contact any Customers who may be affected.
Warranty as stated in Encompass Terms and Conditions of Trading is void if any modification is made to the warranted product.
Plan view of VMS Support and Spacers
VMS3-10 Busbar Support
3 Pole assembly – versatile mounting